And at the Casper Airport has created the need for Rocky Mountain Power to apply to the
Download 9.48 Kb.Pdf просмотр
- Навигация по данной странице:
- Exhibit 1
and at the Casper Airport has created the need for Rocky Mountain Power to apply to the
Commission for a CPCN so that the following infrastructure can be added to its substation and
A new 115kV three breaker ring bus Bar Nunn substation to be located on five acres
approximately one mile west of the town of Bar Nunn.
substation to the new Bar Nunn substation.
In order to adequately serve existing and new customers in the Casper and Bar
Nunn areas and to generally meet the growing energy demands in the vicinity of the Casper
Airport, the Company proposes to construct the new Bar Nunn substation with a three circuit
breaker ring bus supporting two power transformers and nine distribution circuits. This is
explained in detail in Exhibit 1, the master plan of the new Bar Nunn substation. The initial
construction will include one circuit breaker, one 115kV–12.5kV, 30MVA power transformer
and three distribution circuits. Exhibits 2, 3 & 4 contain the general plan, electrical one-line
diagram and profile view illustrating the initial Bar Nunn substation configuration
115 kV transmission line project as a general system improvement, which is estimated to cost
approximately $10.3 million. The Company will use a reasonable balance of debt and equity to
finance the project. There are no customer specific financial advances in aid of construction
related to this project.
owned by Rocky Mountain Power. The land on which the 4.16 miles of 115kV transmission line
Do'stlaringiz bilan baham:
ma'muriyatiga murojaat qiling